Heat flows in direction of decreasing temperature, i.e., from high-temperature to low temperature regions. The transfer of heat from a low-temperature to high-temperature requires a refrigerator and/or heat pump. Refrigerators and heat pumps are essentially the same device; they only differ in their objectives. The performance of refrigerators and heat pumps is expressed in terms of coefficient of performance (COP):
The Reversed Carnot Cycle
Reversing the Carnot cycle does reverse the directions of heat and work interactions. A refrigerator or heat pump that operates on the reversed Carnot cycle is called a Carnot refrigerator or a Carnot heat pump.
Fig. 5-1: T-s diagram and major components for Carnot refrigerator.
The reversed Carnot cycle is the most efficient refrigeration cycle operating between two specified temperature levels. It sets the highest theoretical COP. The coefficient of performance for Carnot refrigerators and heat pumps are:
M. Bahrami ENSC 461 (S 11) Refrigeration Cycle 1
The Carnot cycle cannot be approximated in an actual cycle, because:
1- executing Carnot cycle requires a compressor that can handle two-phases 2- also process 4-1 involves expansion of two-phase flow in a turbine.
The Ideal Vapor‐Compression Refrigeration Cycle
The vapor-compression refrigeration is the most widely used cycle for refrigerators, air-conditioners, and heat pumps.
Fig. 5-2: Schematic for ideal vapor-compression refrigeration cycle.
Assumptions for ideal vapor-compression cycle:
irreversibilities within the evaporator, condenser and compressor are ignored no frictional pressure drops refrigerant flows at constant pressure through the two heat exchangers (evaporator
heat losses to the surroundings are ignored compression process is isentropic
M. Bahrami ENSC 461 (S 11) Refrigeration Cycle 2
Fig. 5-3: T-s and P-h diagrams for an ideal vapor-compression refrigeration cycle.
A reversible, adiabatic (isentropic) compression of the refrigerant. The saturated vapor at state 1 is superheated to state 2.
An internally, reversible, constant pressure heat rejection in which the working substance is de-superheated and then condensed to a saturated liquid at 3. During this process, the working substance rejects most of its energy to the condenser cooling water.
An irreversible throttling process in which the temperature and pressure decrease at constant enthalpy. The refrigerant enters the evaporator at state 4 as a low-quality saturated mixture.
An internally, reversible, constant pressure heat interaction in which the refrigerant (two-phase mixture) is evaporated to a saturated vapor at state point 1. The latent enthalpy necessary for evaporation is supplied by the refrigerated space surrounding the evaporator. The amount of heat transferred to the working fluid in the evaporator is called the refrigeration load.
The ideal compression refrigeration cycle is not an internally reversible cycle, since it involves throttling which is an irreversible process. If the expansion valve (throttling device) were replaced by an isentropic turbine, the refrigerant would enter the evaporator at state 4s. As a result the refrigeration capacity would increase (area under 4-4s) and the net work input would decrease (turbine will
M. Bahrami ENSC 461 (S 11) Refrigeration Cycle 3
produce some work). However; replacing the expansion valve by a turbine is not practical due to the added cost and complexity. The COP improves by 2 to 4% for each °C the evaporating temperature is raised or the condensing temperature is lowered.
Actual Vapor‐Compression Refrigeration Cycle
Fig. 5-4: T-s diagram for actual vapor-compression cycle.
Most of the differences between the ideal and the actual cycles are because of the irreversibilities in various components which are: 1-In practice, the refrigerant enters the compressor at state 1, slightly superheated vapor, instead of saturated vapor in the ideal cycle. 2- The suction line (the line connecting the evaporator to the compressor) is very long. Thus pressure drop and heat transfer to the surroundings can be significant, process 6-1. 3- The compressor is not internally reversible in practice, which increase entropy. However, using a multi-stage compressor with intercooler, or cooling the refrigerant during the compression process, will result in lower entropy, state 2’. 4- In reality, the refrigerant leaves condenser as sub-cooled liquid. The sub-cooling process is shown by 3-4 in Fig. 5-4. Sub-cooling increases the cooling capacity and will prevent entering any vapor (bubbles) to the expansion valve. 5- Heat rejection and addition in the condenser and evaporator do not occur in constant pressure (and temperature) as a result of pressure drop in the refrigerant.
Selecting the Right Refrigerant
When designing a refrigeration system, there are several refrigerants from which to choose. The right choice of refrigerant depends on the situation at hand. The most common refrigerants are: R-11, R-12, R-22, R-134a, and R-502. R12: CCl2F2 dichlorofluoromethane, used for refrigeration systems at higher temperature
levels- typically, water chillers and air conditioning (banned due to ozone layer effects)
M. Bahrami ENSC 461 (S 11) Refrigeration Cycle 4
R22: CHClF2 has less chlorine, a little better for the environment than R12 - used for
lower temperature applications R134a: CFH2CF3 tetrafluorethane - no chlorine- went into production in 1991-
replacement for R12 Ammonia NH3: corrosive and toxic- used in absorption systems-cheap- high COP R744: CO2 behaves in the supercritical region- low efficiency R290: propane combustible. Many factors need to be considered when choosing a refrigerant:
ozone depletion potential ,global CFC (chlorofluorocarbons) refrigerants allow warming potential:
more ultraviolet radiation into the earth’s
atmosphere by destroying the protective ozone layer and thus contributing to the greenhouse effect that causes the global warming. As a result the use of some CFCs (e.g. R-11, R-12, and R-115) are banned by international treaties.
the refrigerant saturated pressure at the evaporator should be above Patm.
1- the heat of vaporization of the refrigerant
should be high. The higher hfg, the greater the
refrigerating effect per kg of fluid circulated.
2- the specific heat of the refrigerant should be
low. The lower the specific heat, the less heat
it will pick up for a given change in temperature during the throttling or in flow
through the piping, and consequently the
greater the refrigerating effect per kg of refrigerant 3- the specific volume of the refrigerant should be low to minimize the work required per kg of refrigerant circulated since evaporation and condenser temperatures are fixed by the temperatures of the surroundings 4- selection is based on operating pressures in the evaporator and the condenser.
Other desirable characteristics of refrigerant are: non-flammable, being chemically stable, and be available at low cost.
M. Bahrami ENSC 461 (S 11) Refrigeration Cycle 5
Cascade Refrigeration Cycle
Systems that have 2 (or more) refrigeration cycles operating in series.
Fig.5-5: A 2-stage cascade refrigeration cycle.
Cascade cycle is used where a very wide range of temperature between TL and TH is
required. As shown in Fig. 5-5, the condenser for the low temperature refrigerator is used as the evaporator for the high temperature refrigerator. Cascading improves the COP of a refrigeration cycle. Moreover, the refrigerants can be selected to have reasonable evaporator and condenser pressures in the two or more temperature ranges.
M. Bahrami ENSC 461 (S 11) Refrigeration Cycle 6
Fig. 5-6: T-s diagram for 2-stage cascade system.
The two cycles are connected through the heat exchanger in the middle, which serves as evaporator (cycle A) and condenser (cycle B). One can write:
Figure 5-6 shows the increase in refrigeration capacity (area under 4-7’) and decrease in compressor work (2-2’-6-5).
Example 5-1: A two-stage Refrigeration cycle
Consider a two-stage cascade refrigeration system operating between pressure limits of 0.8 and 0.14 MPa. Each stage operates on an ideal vapor-compression refrigeration cycle with refrigerant R-134a as working fluid. Heat rejection from the lower cycle to the upper cycle takes place in an adiabatic counter flow heat exchanger where both streams enter at about 0.32 MPa. If the mass flow rate of the refrigerant through the upper cycle is 0.05 kg/s, determine:
a) the mass flow rate of the refrigerant through the lower cycle b) the rate of heat removal from the refrigerated space and the power input to the
M. Bahrami ENSC 461 (S 11) Refrigeration Cycle 7
1) Steady operation 2) ∆KE=∆PE=0 3) Adiabatic heat exchanger.
Figure 5-6 shows the T-s diagram for the cascade cycle. Enthalpies for all 8 states of refrigerant R-134a can be read off Tables A-12 and A-13. Writing energy balance for the heat exchanger, the mass flow rate of the refrigerant through the lower cycle can be found:
m A h mB h m A h mB h
95 47kJ / kg mB
b) the heat removal by the cascade cycle can be determined from:
W in W Comp ,1in W Comp2,in m A h h
M. Bahrami ENSC 461 (S 11) Refrigeration Cycle 8
ISDH Long Term Care Newsletter Issue # 10-15 September 24, 2010 In Today's Issue: - ISDH Staffing Update - Security Advisory - CMS Updates - Emergency Preparedness - Director of Women's Health - Recalls - Coming Events The Indiana State Department of Health (ISDH) would like to provide an agency staffing update for theDivision of Long Term Care. Attached is a the long